|Question: 09-14||Code Section: 7||Date: 14 September 2009||OBC 2006 Reference: 18.104.22.168.(1)|
Question: A sewage tank with a 3″ vent … would a 1 1/2″ waste from a laundry tub fixture be allowed to discharge into the vent.
Interpretation: No, an ejector vent cannot be wet vented, nor can its vent serve as a wet vent. 22.214.171.124.(1) states that only a fixture served by a soil or waste pipe can serve as a wet vent.
Interpretation: Approved at AMES 2009