|Question: 05-16||Code Section: 7||Date:||OBC 2006 Reference:|
Question: Is there a data/ info base that I can access for other acceptable ways on part 7, plumbing ie: island sinks for venting?
Interpretation: (On. Reg. 403/97) First part – other info available? Don’t know of any databases, but suggest running the vent below the floor joists just like a tub or shower but be careful of 184.108.40.206(1):
Second part, first drawing – add cleanout upstream of trap to try and satisfy 220.127.116.11.(3) and Second drawing – does not meet 7.5.4.(2) and 18.104.22.168.(1).