|Question: 09-14||Code Section: 7||Date: 14 September 2009||
OBC 2006 Reference: 220.127.116.11.(1)
Question: A sewage tank with a 3" vent ... would a 1 1/2" waste from a laundry tub fixture be allowed to discharge into the vent.
Interpretation: No, an ejector vent cannot be wet vented, nor can its vent serve as a wet vent. 18.104.22.168.(1) states that only a fixture served by a soil or waste pipe can serve as a wet vent.
Interpretation: Approved at AMES 2009