|Question: 14-02||Code Section: 7||Date: 21 January 2014||
OBC 2012 Reference: 18.104.22.168.
- I know table 22.214.171.124 states your only permitted 3 F.U. on a 2” wet vent But because the 3” stack is only 6” away would the W.C. not be stack vented as well?
- Could this installation pass?
Interpretation: NO. The WC is not stack vented as it is not the most downstream fixture as per 126.96.36.199(1)(d).
In addition, the total load on the branch connected to the WC trap arm is over 2 fu’s, as permitted by 188.8.131.52.(1) (f).